Dilution is the process of decreasing the concentration of a solute in a solution, usually simply by mixing with more solvent like adding more water to the solution. To dilute a solution means to add more solvent without the addition of more solute. The resulting solution is thoroughly mixed so as to ensure that all parts of the solution are identical.
For example, if there are 10 grams of salt (the solute) dissolved in 1 litre of water (the solvent), this solution has a certain salt concentration (molarity). If one adds 1 litre of water to this solution the salt concentration is reduced. The diluted solution still contains 10 grams of salt (0.171 moles of NaCl).
Mathematically this relationship can be shown by equation:
- c1 = initial concentration or molarity
- V1 = initial volume
- c2 = final concentration or molarity
- V2 = final volume
Basic room purge equation
The basic room purge equation is used in industrial hygiene. It determines the time required to reduce a known vapor concentration existing in a closed space to a lower vapor concentration. The equation can only be applied when the purged volume of vapor or gas is replaced with "clean" air or gas. For example, the equation can be used to calculate the time required at a certain ventilation rate to reduce a high carbon monoxide concentration in a room.
Sometimes the equation is also written as:
- Dt = time required; the unit of time used is the same as is used for Q
- V = air or gas volume of the closed space or room in cubic feet, cubic metres or litres
- Q = ventilation rate into or out of the room in cubic feet per minute, cubic metres per hour or litres per second
- Cinitial = initial concentration of a vapor inside the room measured in ppm
- Cfinal = final reduced concentration of the vapor inside the room in ppm
Dilution ventilation equation
The basic room purge equation can be used only for purge scenarios. In a scenario where a liquid continuously evaporates from a container in a ventilated room, a differential equation has to be used:
where the ventilation rate has been adjusted by a mixing factor K:
- C = concentration of a gas
- G = generation rate
- V = room volume
- Q′ = adjusted ventilation rate of the volume
The dilution in welding terms is defined as the weight of the base metal melted divided by the total weight of the weld metal. For example, if we have a dilution of 0.40, the fraction of the weld metal that came from the consumable electrode is 0.60.
- Displacement ventilation
- Reaction rate
- Partial molar quantities
- Apparent molar property
- Excess molar quantity
- Heat of dilution